2-10. PUMP AND HOUSING ASSEMBLY - lNSPECT/REPLACE/REPAIR (Cont)
3. INSPECT/REPAIR CABLE ASSEMBLY
Remove insulator boot (11) from positive lead.
Visually inspect insulator boot (11) for cuts, crack-
ing, or other damage. Replace damaged boot.
Using a multimeter, check for continuity between
lug terminal (12), and end of white negative wire
lead. If open, replace ground wire terminal and
heat shrink tube (13) (Item 1, Appendix B, Bulk
Items List). Crimp both cable shield wire and
ground wire in new lug terminal (12).
Using multimeter, check between terminal (14)
and end of black positive wire lead. If open, re-
place terminal (14).
Check general condition of all wiring. If wiring or
heat-shrink tubing is cracked, broken, or other-
wise damaged, repair as necessary.
Apply a thin coating of petrolatum (Item 6, Ap-
pendix C) to preformed packings (10). Install
smaller preformed packing into top groove, and
remaining packings in lower two grooves in
GO TO NEXT PAGE