Section III. SPECIAL TOOL AND SPECIAL TEST EQUIPMENT REQUIREMENTS
No Special Tools or Test Equipment Required.
Section IV. REMARKS
Reface valves and seats
Air Test for leaks
Drain and Flush at seasonal changes
Straighten and weld
Test for proper operation
Test to assure that the proper specific gravity is maintained
Test for and correct, interference emission
Test for improper readings
Performance: After initially filling the case the pump operating at 2600 RPM shall:
a. Prime in not more than 1 minute when subjected to a static suction lift equivalent to 10 feet using 15 feet of
suction line and one elbow.
b. Deliver not less than 980-1000 GPM 6 60 feet total head.
c. After conducting tests (a and b) above, test the pump check valve-shut off the pump and allow it to set for
not less than 30 minutes. Restart the pump and determine if the pump immediately primes. Immediate prime
is an indication that the valve prevents siphoning of water from the pump case.
Replace seals and gaskets.