1 0 - 3 8 3 5 - 2 1 9 - 1 4
5-6. Flow Control Kit Chest Assembly.
This task consists of:
M a t e r i a l s / P a r t s ( c o n t)
Drill (Appendix B, Section Ill, Item 2)
Rivets (Refer to TM 10-3835-219-24P)
Riveter (Appendix B, Section Ill, Item 3)
E q u i p m e n t C o n d i t i on
M a t e r i a l s / P a r ts
Kit components removed (para 3-7)
Solvent, Dry Cleaning (Item 7, Appendix E)
Rags, Wiping (Item 5, Appendix E)
R e p a i r. (figure 5-2)
The flow control kit chest assembly is made up of three chest assemblies.
One chest assembly for Model ADC-1200 and two chest assemblies for
Model 1461. Components of the flow control kit for Model FIHK-100 are
contained in one chest assembly. The size of each chest assembly varies.
The repair of each chest assembly is the same.
Inspect all components and chest assembly and replace if damaged.
Drill out rivets (1) on each side of chest and disconnect lid supports (2).
While supporting lid (3), drill out rivets (7) attaching hinge (5) to chest (6) and remove lid.
Place lid (3) on bench and drill out rivets (7) attaching hinge (5) to lid (3).
Drill out rivets (8) on each side of lid and disconnect lid support (2) from lid (3) and remove
s u p p o r t.
Drill out rivets (9) attaching handles (10) to chest (6) and remove handles.
Drill out rivets (11) attaching lower latch half (12) to chest (6) and remove latch half.
Drill out rivets (13) attaching upper latch half (14) to lid (3) and remove latch half.
Weld any cracks, breaks or holes in chest (6) and partitions (15)
W A R N I NG
Dry cleaning solvent used to clean parts is potentially dangerous to
personnel and property. Avoid repeated and prolonged skin contact.
Do not use near open flame or excessive heat. Flash point of solvent is
Clean all items with dry cleaning solvent, and dry thoroughly.